Floor Standing Rack Cabinet
i-View 19” rack cabinets are designed for high quality equipments and standards
Most of Network Component manufacturers are able fit their equipment in 19” wide Racks. The table and diagram on the following page outlines the compliance speciation in detail and provides a representation
19” Rack Specication
A rack’s mounting _xture consists of two parallel metal strips (referred to as “rails”) standing vertically. The rails are separated by a gap of 450 mm (17.72 inch) and are a minimum of 16.7 mm (0.657 inch) wide, giving an overall rack width of 482.6 mm or 19 inch, as the name suggests.
The rails have holes at regular intervals, with both rails matching, so that each hole is part of a horizontal pair with a centre to centre distance of 465mm (18.3 inch). The holes are arranged vertically in repeating sets of three, with centre to centre separations of 12.7 mm
(0.5 inch), 15.875 mm (0.625 inch) and 15.875 mm. The hole pattern repeats every 44.45 mm (1.75 inch). Racks are divided into regions that are 44.45 mm in height. Within this region commonly referred to as an “RU” or “U”, there are three complete hole pairs in a vertically symmetric pattern that are centered 6.4 mm (0.25 inch), 22.2 mm (0.875 inch) and 38.1mm (1.5 inch) from the
top or bottom of the RU.
W×D×H mm Capacity 600×600×992 18U 600×800×992 18U 600×900×992 18U 600×960×992 18U 600×600×1081 22U 600×800×1081 22U 600×900×1081 22U 600×960×1081 22U 600×600×1303 27U 600×800×1303 27U 600×900×1303 27U 600×960×1303 27U 600×600×1525 32U 600×800×1525 32U 600×900×1525 32U 600×960×1525 32U 600×600×1748 42U 600×800×1748 42U 600×900×1748 42U 600×960×1748 42U 600×600×2192 47U 600×800×2192 47U 600×900×2192 47U 600×960×2192 47U